Posted on 20-Jul-2020
Aquamaster Water Treatment Ltd
One of my customers in Bedfordshire requested a service call. All the well water booster delivery pumps had stopped working. I carried out a few checks on the well water system, l discovered that the pressure sensor controller was not giving a signal to bring on the pumps. I removed the faulty pressure sensor and replaced it with a new one. After turning the electric back on, the well pumps started to pump the water once again. This problem can be quite common with well water or borehole water systems that have a lot of iron in the water. The iron will block up the water treatment system quite quickly. It is necessary to have regular servicing carried out.