Posted on Feb 18, 2021
Aquamaster Water Treatment Ltd
BWT Waterside water softener repairs Cambridgeshire. We had a call from a customer regarding a leaking water softener. The salt tank was full of water and overflowing out of the overflow pipe. After taking the cover off of the softener valve, l could see that there was quite a leak coming from the valve. This is a common problem with the Waterside rotary valves, they all suffer from this problem. After stripping down the valve head and replacing the large O ring, the system was tested and left in working order.